The fueling station tank shall be an above ground, skid mounted, "pre-packaged" fueling station, double-walled, 5,000 gallon capacity, and ballistic proof. The skid shall be anchored to a new concrete foundation. The concrete foundation design shall be prepared and stamped by a structural engineer licensed in state of Michigan. A TopKAT Fuel Management System Smart Key Panel will control the fuel system. The fuel tank, pumps, pumps, dispensers and related equipment shall be skid mounted and provided as a turn-key system. The design shall provide for an integrally constructed and fabricated, tested and certified system prior to delivery to the VA site. The tank shall contain a product decal specific to the site. Where required, containment structures shall be constructed of steel-reinforced concrete. Brick wall that aesthetically matches with the surrounding buildings and structures, enclosing the rear, right and left side of the fuel tank, providing adequate space for maintenance of the tank and associated fueling components. Overhang that protects the pump and fuel station users from inclement weather. Provide on-demand, monitoring and reporting of actual fuel consumption, vehicle ID, odometer reading, date of fueling and gallons dispensed. Date of fuel transport shall be included.Will include a TopKAT card reader/fuel management system capable of authorizing and recording both fuel and fuel transactions using the General Services Administration (GSA) Smart fuel cards processing system. The controller shall be compatible with the GSA controller to assist in the reimbursement for the E85 fuel. The system shall be connected to one or more remote billing services by telephone modem for a high speed line, for the purpose of remotely authorizing, recording, and billing transactions by fuel networks. And include setting up the remote billing accounts. The E85 Fueling Station shall include clearance warning signs, where appropriateThe work performed will be at the Aleda E. Lutz, Saginaw VA Medical Center1500 Weiss St., Saginaw, Michigan, 48602.The solicitation will be issued as an "Invitation for Bid" (IFB) conducted in accordance with FAR Parts 14, 19, and 36 and be evaluated in accordance with the procedures therein. The IFB will be a 100% set-aside for SERVICE DISABLED VETERAN OWNED SMALL BUSINESS (SDVOSB). The applicable NAICS code is 237120 with a size standard of $33.5 million. The IFB will be issued on or about March 3, 2014 and proposals will be due on or about April 4, 2014 at 2:00PM (EDT), at 6150 Oak Tree Blvd, Suite 300, Independence, Ohio, 44131. The Government intends to award a firm-fixed-price contract. The period of performance shall be 180 days from the Notice to Proceed issue date. This notice is not a request for competitive offers. Magnitude of Construction is expected to be between $250,000 and $500,000. The point of contact is Samantha Mihaila who can be reached by email at Samantha.Mihaila@va.gov Questions may be submitted by e-mail to above point of contact. Telephone calls will not be accepted. PCAC reserves the right to use only FBO, via the internet, to provide notification of any amendments to this IFB. It is the contractor's responsibility to view the FBO website daily for any amendments to the IFB.